Year : March 2019
Raw water is well water in Romania, water quality exceeding the standard factors are ammonia (micro-super), chloride (micro-super), residual chlorine (micro-super), turbidity (severely exceeding the standard), total number of mites (micro-super), nitrite (micro-super). For ammonia, due to the slight excess, with oxidation (fungicides) and quartz sand can solve the problem, the total number of places (micro-super) equipped with sterilization equipment can be resolved, turbidity is removed through quartz sand, because nitrites and nitrates, chlorides are micro-super, Resolve the problem by ultrafiltration plus reverse osmosis.
Our company adopts each set of ultrafiltration system and reverse osmosis system, and adopts integrated equipment of containerized structure.
Ultrafiltration produced 11m3/H, RO system produced 12m3/H, and the produced water was mixed and drunk.
The system's recovery rate was 74.2%.
Raw water tank → raw water pump → quartz sand filter → activated carbon filter → security filter → ultrafiltration system → production water tank .
Reverse osmosis system：
Raw water tank → raw water pump → quartz sand filter → security filter → reverse osmosis system → production water tank.
Ultrafiltration equipment and RO equipment use a set of cleaning system.
Electric control system: automatic control.
Container: 40 "HQ FLC.
Story of us was since 2007.
Jinhuimo is meeting a global need for clean water through membrane technology treatment solutions.